|Home||» Products||» ONLINE UPS||» DEEP Impact 1 KVA UPS|
The deep impact from the house of UTL is a relatively new concept in the power sector. The deep impact of ups from the house of UTL packs all the features of an online ups in a compact form factor, further being transformer less the deep impact is extremely light and portable, making it easily installed in homes or even in offices. UTL’S DEEP impact range of online ups is a powerful, affordable and reliable backup option for your appliances
Available from the ranges of 1 to 3 KVA in the DC voltages 12 & 36 volts the deep impact range of ups is a product that is capable of taking care of the backup needs of your computers along with the other appliances.
1 KVA in 12Volts & 36Volts
2 KVA & 3KVA IN 48 Volts and 72 Volts resp. (in R&D)
Output short-circuit protection.
When there is a short-circuit in output load, the system goes into Output short-circuit protection i.e. the system will shut down.
MOSFET short-circuit protection.
When we try to start the system when it is already in protection mode, the system goes into MOSFET short-circuit protection. It means that the system will not start in this condition, if the short-circuit has not been removed.
Output over voltage protection.
Whenever the output voltage goes higher than the prescribed value, the system goes into Output over voltage protection.
When the Load is more than 105% of the rated Load, the system goes into Overload protection. If the system is in battery mode, then after 30 sec, system will shut down and if the system is in Mains mode, then the load will be shifted on Mains.
Battery low protection.
Whenever the battery voltage goes below 10V, the system goes into Battery low protection. This prevents deep discharge of the battery.
Input AC over / under voltage protection.
Whenever the Input voltage is out of range, the system goes into “Input AC over / under voltage protection” and moves to battery mode.
Over Temperature protection.
When the system temperature goes above 80 °C, the system goes into Over Temperature protection i.e. the system will shut down.
Reverse phase protection.
When the Input Mains Phase is reversed, the system goes into Reverse phase protection.
Battery reverse protection (through fuse)
When we connect the battery in reverse polarity or the battery wire is shorted, the system goes into Battery reverse protection.
Charging short-circuit protection.
When the charging is going on, and the battery is shorted, the system goes in to Charging short-circuit protection. Tis means that the charging voltage will become zero and the charging resumes after the short is removed.
|Power Rating||1 KVA (12V , 36V) ; 2KVA (48V) ; 3KVA (72V)|
|Voltage Range||Single Phase - 22O V + 20 %|
|Frequency||50 Hz + 5%|
|Input Power Factor||> 0.95|
|Electrical Connection||6A, Indian Lead|
|Voltage||Single Phase - 220V , 230V|
|Frequency||50 Hz + 0.05%|
|Wave Form||Sine Wave|
|Transient Response||<8(10%~90% Linear Load)|
|Voltage Harmonic||< 3 % (Linear load)|
|Overload Capacity||110% 30 sec, 111 to 150% : 18 sec, >150% :1 sec|
|LED||Battery ON # Battery Low # Overload # Bypass # Mains High # Mains ON|
|LCD Meter||Output (Voltage & Frequency) # DC Voltage # Input (Voltage &Frequency) # Battery status # Load level|
|Db9 / USB||RS232 (Optional)|
|Efficiency (AC-AC)||> 85**(FULL LOAD)|
|Transfer time||0 ms|
|Temperature||0 ~ 45 `C|
|Humidity||5-95 %(Non -Condensed)|